One of our power distribution units in Reynolds House has restarted several times, including de-powering and re-powering connected devices several times. Some customers whose equipment was powered from a single feed will have lost power.
PDU failure in Reynolds House Colocation and Dedicated
- Event Started
- 2019-10-28 06:05
- Report Published
- 2019-10-28 02:33
- Last Updated
- 2022-04-13 09:35
- Event Finished
- 2019-10-29 23:30
Timeline (most recent first)
Our engineers are leaving site. This maintenance is complete and has been a success.
Our engineers have removed the failing PDU and worked with the datacentre technicians to commission the replacement PDU. We are monitoring the situation before we begin to close this maintenance out.
Engineers have arrived on site and are about to begin work.
A replacement PDU has been ordered and should arrive tomorrow. Maintenance to swap out the failed unit has been provisionally arranged for 18:00-20:00 2019-10-29.
The PDU continues to show random power outlets as down each time we query its status. While we do not believe that it is actually power-cycling those ports, we do not trust it to continue behaving and so have moved all single-powered devices off that PDU and onto the other PDU in that rack.